- Country of manufactureRussia
Borehole WWSystem 1 adapter
Borehole WWSystem adapter
The borehole adapter is adaptation which is used for making of the water pipes passing from the well to the building. It represents fine and, perhaps, the only alternative to the device under the name a caisson (which besides the enormous sizes and costs expensive very).
The borehole adapter is a design which part three removable parts are. They unite at one level: one from outer side of casing pipe, and two from internal. Tasks which this device is capable to solve often depend on correctness of its use and installation. For this purpose it is necessary to enter a pipe which will be responsible for water supply from the pump to the room where the operational column of the well, at a special depth will be located. It is very important factor: depth has to exceed height of frost penetration in the soil. For Moscow and area this parameter makes about 1,4-1,5 m. Such arrangement provides free use of a product even in the most severe winter.
It is possible to install the soaking-up branch pipe from the station of water supply on this device in case the intake of water is made from the well which depth makes no more than eight meters. Other nuance at installation of such equipment is need of preservation of tightness of a pipe of the well. It becomes to limit a possibility of hit of sewage. Also it will help to accelerate possible process of dismantle of a submersible pipe or the pump, through it from the water-bearing horizon there is a water raising. If it is established works correctly, it is more than any expenses and extras it is not required. It turns out that use of the borehole adapter helps to use all highway, allowing not to worry about its frost penetration during the winter periods, and also to repair and serve both the well, and the pump shipped in it. Therefore it is possible to tell safely - this device is intended for simplification of installation and considerable economy of means. You can directly buy the borehole WWSystem adapter in Moscow on our website.
Instruction for installation of the borehole adapter
Principle of operation of the adapter very simple. Thanks to simplicity of its device and a malogabaritnost, both of its bezrezbovy parts are connected to the help of "larkspur" connection which serves as the holding connection when there is an immersion of the pump to the well. In addition, it is capable to provide a high density prileganiye of both parts to each other. The sealing rubber ring located on a removable half of the device provides high tightness of all connection. The half given it is taken out from the well along with the pump. For implementation of equipment maintenance on the top part the cut carving is provided. At the same time it is possible to twist the special device in it – a stripper which represents a sawn-off shotgun of a steel pipe with a necessary diameter on which the carving is also cut. Convenience of this equipment consists also that you do not need to endure more about plum of water from all system in the winter, even in case you do not plan to heat the room throughout all season. In that case it is necessary just to separate parts of the adapter, and water from a water supply system without any efforts will merge back to the well.
The product Malogabaritnost is fine help for its installation too. As there are cases when the point of drilling settles down absolutely close from any highway that in turn makes impossible installation of other equipment. Thanks to high tightness of this device, it is capable to sustain water pressure in all system to eight atmospheres. It is provided thanks to a sealing ring which connects a carving in connection.
However if installation for several buildings at the same time is planned, it will be necessary to consider a possibility of giving of more high pressure – it can lead to dribble in a junction. But the sealing ring in itself is a removable detail so replacement represents it simple process.
Excellent resistance to different types of corrosion provides very long term of operation of the device at the correct use. It is possible to increase it by means of installation of the corrosion-proof copper pipes or pipes made of special alloy of steel, directly in the house.
It is necessary to consider the following feature at installation of this device: a part of the adapter will settle down in pipe space therefore also it is necessary to pick up diameter of a column on 1,5 or 2 cm more, than diameter of the pump. At service of the adapter it is necessary "to pull off" its connections for prevention of possible installation at least once a year.
Borehole adapters are manufactured of various materials, generally it is brass, bronze, and also stainless steel. The sizes of this device differ in a big variety because the device received huge popularity and is used for performance of the most different tasks. The borehole adapter which price is several times lower, than at other products can be bought from us on the website right now. Address our experts, and you right there receive answers to all questions, important for you.
With these goods buy: