EKOTs installation represents a simple monoblock design. Main knots of the device: radial BP 80-75 fan and electroheater of EKO. Among themselves these elements connect by means of the diffuser to the flexible sheaf helping to compensate vibration.
EKOTs is equipped with a welded frame which fastens to the base or overlapping of the building by means of anchor bolts. To reduce the level of vibration use of the additional vibroextinguishing laying is possible. Installation is intended for heating of the stitched air which is carried out thanks to work of tubular heating elements (TENOV). Placement TENOV differs depending on execution of a heater (from one to four sections). To improve a thermolysis between electric heaters and stitched air use aluminum fins.
Each TEN is connected to an electric circuit, among themselves heaters connect in "star". What allows to reach the maximum power. EKOTs is capable to work for 100%, 66,7%, 50% and 33,3% of rated power, depending on a standard size. The EKOTs air-heating installation can be completed with a case of management by means of which management and control over operation of the unit is made. It helps to protect installation from an overheat, short circuits, overloads on current and other possible problems.
Purpose of the EKOTs installations
EKOTs found application in rooms with a significant area: workshops, shops, warehouses, on farms and in other production constructions. They are used as effective vozdushnootopitelny installations. In working air environment there should not be explosive particles, and conducting dust can be present only at insignificant quantity. Average annual concentration of dust in air should not exceed 1mg/m ³.
Short-term increase of dust content to 10 mg/m ³ is allowed. Service conditions Operation of installation is possible in the conditions of a frigid and temperate climate with the fourth category of placement in accordance with GOST (placement in the enclosed space with artificial regulation of microclimatic conditions). Range of working temperatures from - 10C ° to + 40C °. Electrocalorifer installation in the certain room or in extensions is placed.