Installation for processing of the UVM 10-10 transformer oil, is intended for decontamination, cleaning of mechanical impurity, nitriding and heating of the transformer oil which is filled in in power transformers up to 1150 kV inclusive.
Installation can be used for heating of oil-filled electric devices by hot transformer oil, and also for pumping out of power transformers.
Installation is applied in the assembly, repair and operational organizations which are engaged in processing of transformer oil.
Installation is executed in the form of the container with the protection cover and doors closed on the lock.
Installation is made in a climatic modification of U1 in accordance with GOST 15150.
Installation is not suitable for work in the explosive, poisoning, reacting with lubricants Wednesdays.
At application of installation in the enclosed space it is necessary to provide removal of the pumped-out gases in the atmosphere by means of pipelines.
Technical characteristics of installation
|Productivity, m3/hour, no more|
|- in the decontamination mode||10|
|- in the heating mode||15|
|Parameters of the processed oil:|
|- volume gas content of oil of %, no more||0,1|
|- mass moisture content of oil, g/t, no more||10|
|- subtlety of a filtration, micron, no more||10|
|The maximum temperature of oil at the exit in the heating mode, ºС||85|
|Pressure at the exit, MPa||0,2|
|Power of a maslonagrevatel, kW||150|
|Maximum power consumption, kW||185|
|Residual pressure in a vacuum column in the course of decontamination, Pa, no more||399|
|Residual pressure in a vacuum column when checking on tightness, Pa, no more||39,9|
|Natekaniye when checking on a vakuumplotnost in 1 hour, Pa no more:||266|
|Parameters of electric current|
|- tension, In||220/380|
|- variable with a frequency, Hz||50|
|Overall dimensions, mm no more|
|Weight, kg, no more||3800|