- BrandНПП «МАГНИТО-КОНТАКТ»
- Country of manufactureRussia
Declaration of conformity to the requirements of the Technical Regulations of the Customs Union "On the safety of low - voltage equipment" (TR CU 004/2011), the Technical Regulations of the Customs Union "Electromagnetic compatibility of technical means" (TR CU 020/2011) EAEU N RU D - RU. НР15.V. 08437/20 . Valid from 5.10.2020 to 4.10.2025
1.1. General information
You can buy a connecting box KS - 2, KS - 3, KS - 4 from us for 4x2 wires at a low price. Switching terminal box KS - 4 is produced in various colors.
Junction boxes KS - 4 (hereinafter referred to as boxes) are intended for installation of security and fire alarm systems, TV surveillance to alarm loops, as well as installation of other DC or AC circuits. Junction boxes KS are produced in three modifications: KS - 2, KS - 3, KS - 4 and several colors:
P / P
|MODIFICATION TYPE||FEATURE OF DESIGN||DEGREE OF PROTECTION AGAINST EXTERNAL IMPACT ACCORDING TO GOST 14254|
|1||KS - 2||2 pairs of terminals||IP40|
|2||KS - 3||3 pairs of terminals|
|3||KS - 4||4 pairs of terminals|
The boxes structurally consist of a base with metal terminals inside. Loop conductors are clamped between terminals and nuts using Ø3mm screws. The base of the KS is closed with a lid and fixed with a self - tapping screw.Fig 1. Dimensions
1.2. Main technical characteristics
|Current through the box contacts||no more than 0.5 A|
|Voltage supplied to the contacts of the box||no more than 50 V|
|Power||no more than 25 W|
|Contact resistance of two contacts||no more than 0.1 Ohm|
|Number of wire connection points||KS - 2 - 4 pcs,
KS - 3 - 6 pcs,
KS - 4 - 8 pcs
|Electrical resistance of insulation between live parts of the box||not less than 20 MOhm|
|Dimensions (fig. 1)||no more: 39 х 39 х 20 mm|
|Box weight||no more than 25 g|
|Protection against external influences according to GOST 14254 - 2015||IP40|
relative humidity no more than 93% at a temperature of 35 ° С
|The box is designed for continuous 24/7 operation|
|The box does not contain precious metals (clause 1.2 of GOST 2.608 - 78)|
|junction box KS||1 PC.|
|passport PASHK.685552.140 PS||1 copy (for packaging)|
1.4. Installation and operating instructions
1.4.1. The installation of the compressor station is carried out according to the relevant normative and technical documentation for the installation, testing and commissioning of security and security and fire alarm systems, communication systems.
1.4.2. The base of the box is attached to the surface with two self - tapping screws. The wires connected to the box contacts must be de - energized.
1.4.3. During operation, the box does not require maintenance.
1.5. Transportation and storage
1.5.1. Transportation conditions must comply with storage conditions 5 in accordance with GOST 15150.
1.5.2. Storage conditions must correspond to storage conditions 1 in accordance with GOST 15150.