KEV electroboilers are intended for application in systems of heating with compulsory circulation and hot water supply of residential and public buildings.
Coppers of KEV are not subject to registration in bodies of Rostekhnadzor.
Heating capacity is 0,43 Gcal/hour
The maximum power is 500 kW
Pressure working - 6 kg/cm2 (0,6 MPas), settlement 10 kg/cm2 (1 MPa)
Smooth regulation of power 1-100
Maximum temperature of heating of water 120 C
Structure and completeness.
The electric boiler block - 1 piece.
Case of management - 1 piece.
The circulation pulser - 1 piece.
Control of the electric boiler is exercised from a case of management in which the protection automatic machine, the contactor and the scheme of automatic equipment are mounted. Devices of control of current loading and tension, and also the protection operating on shutdown of the electric boiler at overloads and short circuits are provided in a power chain.
The scheme of automatic equipment allows to maintain constant water temperature.