Purpose of the RTs-100 installation
It is intended for restoration (regeneration) of the synthetic zeolites applied in installations to an osushka of transformer oil. Installation can be also applied to regeneration of silica gel in thermosiphon filters of the operated transformers. Besides, installation allows to execute the following technological operations:
- drying of capacities for transformer oil;
- drying of firm isolation of power transformers;
- drying of stators of electrical machines.
All specified technological processes are carried out by the deep-drained air with a dew point temperature not above minus 50 °C.
Advantages of the RTs-100 installation
The original scheme of adjustment of power of RTs-100 air heaters, allows to work in the optimum mode of regeneration of adsorbent or heating of dry air.
The built-in compressor of the low pressure (KSh) provides a long autonomous operating mode.
Technical characteristics of the RTs-100 installation
|Productivity on dry air, m3/h, not less||100|
|Temperature of dry air at the exit of installation, °C, not below||400|
|Dew point of the drained air, °C, no more||- 50|
|Time of regeneration (restoration) of zeolite, hours, no more||7|
|Extreme pressure of the drained air at the exit of installation, MPa, no more||0,08|
|Rated capacity, kW, no more||18|
|Supply voltage||380 V, 50 Hz|
|Overall dimensions, mm||1150 x 900 x 2000|
|Weight, kg, no more||850|