The system of the account on the basis of the SATEC BFM136 device allows to carry out measurements of electricity consumption, power, currents, tension on all connected feeders, storage, transfer and display of these data. As the environment of data transmission interfaces RS-232, RS-422, RS-485, Ethernet or the GSM network can be used.
The SATEC BFM136 metering device does not demand direct connection in a rupture of a chain that simplifies installation and service of the device. For connection of the device portable transformers of current like "Rogovsky's belt" are used. Measuring transformers of current of cap type with latches are often used to a bigger convenience of installation.
SATEC BFM136 metering devices allow to adjust up to 16 settings for the organization of record of events at excess or decrease of value of the measured parameter (full, active, jet capacity, current, phase, interphase tension) concerning the set threshold and for record of the measured values on operation of the timer.
SATEC BFM 136 allows to realize record in the memory of 5000 values of six various parameters, and also to carry out information transfer in the *.mdb format. Besides, there is a possibility of data recording in a log. Such magazine contains information on the events connected with internal diagnostics of the device, change of settings and installation of hours, and also dumping of registers and files and operation of programmable settings.
The free software of PAS which is included in the package of delivery of system is applied to data processing about electricity consumption. The software of PAS is installed on the automated workplace (ARME) of the operator of system of the account and allows to configure locally or far off SATEC BFM136 metering devices, on demand to carry out poll of the connected metering devices, to keep and process the necessary volume of data, and also to form necessary reports and printing forms. There is a possibility of export of data.
The decision on the basis of the SATEC BFM136 metering device allows to lower costs of installation and service for the account:
- Economy on the equipment. 12 three-phase metering devices (or 36 single-phase) are more expensive than one SATEC BFM136 device
- Economy of the place for installation. One SATEC BFM136 metering device takes less places, than 12 three-phase metering devices (or 36 single-phase)
- Economy on installation works. Installation of 12 three-phase metering devices (or 36 single-phase) is more expensive than installation of one SATEC BFM136 device
- Economy on operational expenses. Service of one SATEC BFM136 device is simpler and cheaper than service of 12 three-phase metering devices (or 36 single-phase)