Water boiler VC - 10 (for water heating)
|The boiler KV - GM - 0.7|
|Oil burner Baltur TBL 85 P (Italy)|
|The heat exchanger 100 - 60|
|Pump Calpeda NM 50 - 12 FB (Italy)|
|Pump Calpeda NM4 40 / 16B / A, a rate 100grad (Italy)|
|The spring safety valve|
|Storage tank 1.5 m|
|Insulated unit with light box|
|PVC window, door|
|The automation system|
|Fuel tank with visual level control. Volume 600 l|
|water treatment system omagnichivatelem|
|Heat gun for easy start - up and emergency heating|
|Gas burner Baltur (Italy)|
Water heating unit is designed to produce hot water at 65 C and flow 10 m3 / h.
Water heating installation is used in electrified zones (optionally possible to work offline while supplying diesel generator). Placement at a height of over 1,200 m. Above sea level. Climatic version UHL - 1 for supply with the unit - box when shipped without block - Boxing climatic version UHL - 3.
Water plant supplied in a single transportable unit and
assembly associated with the installation of a transportable unit - boxing on planned area of the draft boiler anchor attachment to external networks (heating main, water, sewage, gas, electricity), and assembling the chimney.
Accepted primers should be distending without sagging without swelling and without other adverse conditions with a rated resistance of 0.2 MPa. In the preparation of the site is necessary to provide stormwater drainage. reinforced standard reusable blocks may be used to make foundations for the boiler. You can install the boiler on the strip foundation, all of the implementation of the bases must be drawn up act.
Do not fill cold water heated by the boiler.
In the case of stopping the boiler, recommended piping system and leave the boiler filled with water. Drain water from the boiler should only suspend the boiler at a much longer period and / (or) with a probability defrost system.
Steam boiler plant consists of a boiler, a heat exchanger, pumps, expansion tank, piping and storage container, placed in the insulated unit - boxing.
Block - box has an entrance door with a lock, a window for natural lighting and air flow to the burner. Outside the housing is mounted to the fuel tank. Inside block - Boxing installed water tank and control panel.
The technological process of heating the water
Thermal circuit water heating installation provides domestic hot water with a predetermined temperature range up to 65C. dual heating system.
By operating the circulation pump internal circuit (F1, F4) water enters the boiler, then the water is heated to 100 C and passing through the heat exchanger heats the second kennels WAN (outer F2, F3) to 65 C, if the pump that provides complete heating water in the vessel . When triggered, the pump "on the plant" razogretaja water enters the plant for dosing. Simultaneously, the heat exchanger receives water from the make - up water pipe passed therethrough, is heated and supplied to the water tank.
- To provide the concrete with hot water plant
- Performance of the hot water 10 tons \ h
- Consumption of 16.9 l / hr (diesel) may installing a gas burner
- Mobile unit, fully autonomous
- Time to the operating mode - - 15 minutes
- Italian components (BALTUR burner, valves, safety valves, pumps)
- Automatic control
- Performance of hot water m3 / h 10
- The thermal power of the burner, MW, of at least 0.7
- Diesel fuel consumption min / max, l / h 16.9 . . .72
- The water temperature is not higher 65 ° C
- The volume of water in the boiler, m3 0.9
- The fuel tank 600 l
- The volume of the water tank, l 1500
- Yield on the operating mode, 15 min . . .20
- Weight, kg 4000
- Height, 2540 mm
- Width mm 2260
- Length, mm 6000