- Country of manufactureRussia
- Source of powerGaseous fuel
The gas PG-1000 steam generator on a frame
|The warmed module container with observation ports|
|Tank for BV-7 water heating|
|Copper-steam horizontal liquid-fuel with a covering from stainless steel|
|Gas torch Baltur TBG 85 P (Italy) (optionally diesel)|
|Multistage security system|
|The pump Calpeda (Italy) for pumping water in a copper|
|Reserve pump Calpeda (Italy)|
|Tank for water. Volume is 1 500 liters|
|System of water treatment of water with an omagnichivatel|
|The control panel is automatic|
|Power case of management|
|Passport of PG-1000|
The gas PG-1000 steam generator is intended for work in a complex with concrete plant, carries out the following functions:
- heating of inert sand, crushed stone in RBU bunkers
- heating of concrete plant
- heating of water at concrete plant by production of concrete.
The PG-1000 steam generator, makes steam by means of a steam generator, processing gas fuel.
It is operated generally in cold time, for warming up of sand, crushed stone, PGS and other inert. Steam moves on warming up doziruyushchiyekh the RBU recreation centers complexes that it allows to warm loose.
Gas fuel allows to start easily the RBU steam generator in any frost and to come to the rated power of production of steam.
The PG1000 steam generator represents the boiler on a frame on which the capital equipment is installed: torch, pumps, system of preparation of water, system of automation.
The PG-1000 steam generator is equipped with a gas torch Baltur TBG 85 P (Italy). Optionally the steam generator is equipped with a diesel torch.
All pump equipment installed on the Calpeda steam generator (Italy). Also in a basic complete set the additional reserve pump Calpeda (Italy) is installed.
For more reliable work with different types of water, in a basic complete set the system of preparation of water with an omagnichivatel is already installed.
For work it is necessary to connect electricity of 380 volts and water supply. In an emergency case several days, discharge of water from a steam generator are not required to a stop of RBU or a planned stop.
The PG-1000 steam generator is already ready to work and does not demand carrying out balancing and commissioning and is completely ready to works.
PG-1000 steam generators are not subject to registration in Rostekhnazor's bodies since the working pressure of the steam generator less than 0,07 MPas.Features of installation
- Is not subject to registration In Rostekhnadzor
- Italian gas torch of Baltur (optionally gas)
- Pump equipment Calpeda (Italy)
- System of a vodopogtovka of water with an omagnichivatel
- All copper is made of stainless steel
- The automatic mode, high efficiency — - 90%
- Transport dimensions, does not demand adjustment
- Guarantee 2 years
Characteristics of installation
- Productivity is couple of max, kg ч1000
- Maximum pressure, Mpa0,07
- Temperature of steam is not lower, C°120
- Water volume of a copper, m34,4
- Steam volume of a copper, m31,56
- Look toplivagaz (optionally diesel)
- Fuel consumption, m3 þáß8-40
- Copper fire chamber volume, m30,75
- Area of heating of a copper, m22,1
- Fuel pressure before a copper, Mpa1,0-1,6
- EFFICIENCY, %90
- Weight no more, kg2500
- Height, mm2400
- Width, mm2000
- Length, mm4880