- Country of manufactureRussia
Transformer substation KTP-100
Appointment Of KTP
Complete transformer substations KTP are intended for converting electricity to reduce high voltage 6 or 10 kV to 380 (220) Volt. They are used to supply industrial and household consumers.
For operation substation KTP 100 requires a transformer TM 100/10 (6)/0.4
The main element is the step-down transformer substation power transformer (Oily or dry), which through an input device by senior IOC voltage connects to air or cable input high voltage line. From the low voltage switchgear via RUNN to downward transformer connect electricity consumers.
To protect the transfarmatornoj substation KTP from overloads, short circuits and voltage fluctuations apply dischargers and voltage limiters, as well as circuit breakers or switches with fuses.
To prevent electric shock, attendants and others equipment of substation KTP is housed in a metal or concrete casing equipped with electrical and mechanical locks. Enclosure transformer substation KTP is divided into compartments for high voltage equipment and protection switching, step-down transformer and switchgear low voltage.
To monitor the quality of electric power transformer substation are equipped with test equipment (voltage indicators, instruments for measuring voltage and current) and electricity meters.
When installing substation KTP must comply with the following requirements:
- distance from non-insulated voltage 6-10 kV current-carrying parts shall not be less than 4.5 m and 0.4 kV voltage-not less than 3.5 m.
- measures should be taken to ensure the passage of vehicles between the CRL and the supports of overhead lines.
LLC "PLANT SUBSTATION" draws your attention to the following related products: transformers with audit TM CMG ТМН TMZ TRANSFORMER
TM 100/10 (6)/0.4CMG 100/10 (6)/0.4 TM 100/35/0.4