- Country of manufactureRussia
Transformer substation KTP 63
Appointment Of KTP
Complete transformer substations KTP are intended for converting electricity to reduce high voltage 6 or 10 kV to 380 (220) Volt. They are used to supply industrial and household consumers.
The substations KTP-63 required transformer TM 63 10 (6) 0.4Device KTP
Step-down power transformer-core element of transformer substation. It can be oily or dry. This transformer is connected through an input device, by the higher voltage IOC. Connects oil or dry type transformer for air or cable input high voltage line. Electricity consumers will connect to the reducing the transformer from the low voltage switchgear via RUNN.
To protect the transformer substation KTP from overloads, short circuits, voltage surges, lightning and applied voltage limiters, different switches with fuses, circuit breakers.
In order to avoid the possibility of electric shock, staff, workers and others, our company in the production of KTP, all equipment places in the body, made of metal. This chassis is equipped with electrical and mechanical locks.
Metal transformer, the space is divided into compartments. In one compartment-high-voltage equipment of switching and protection, in another compartment of the step-down transformer and switchgear low voltage.In order to monitor the quality control of electricity, KTP to equip test equipment (such as pointers, voltage devices for measuring voltage and current) and electricity meters. When installing substation KTP you must observe the following rules:
|Distance from non-insulated voltage 6-10 kV current-carrying parts must not be less than 4.5 m and 0.4 kV voltage not less than 3.5 m.||You must delete the passage of vehicles between the KTP and feet of overhead lines.|
OOO "Berezovsky Plant substation recommends you the following related products: transformers with audit transformer CMG, HM, TMZ, ТМН
TM 63 10 (6)/0.4
CMG 63 10 6 0.4