- BrandБерезовский Завод Подстанция
- Country of manufactureRussia
Transformer substation Ktpn 160
Appointment Of KTP
Complete transformer substations KTP are intended for converting electricity to reduce high voltage 6 or 10 kV to 380 (220) Volt. They are used to supply industrial and household consumers.
For the operation you need 160 Ktpn transformer TM 160/10 (6)/0.4Device KTP
Step-down power transformer-core element of transformer substation. It can be oily or dry. This transformer is connected through input device by high voltage IOC. Connects oil or dry type transformer for air or cable input high voltage line.
Electricity consumers will connect to the reducing the transformer from the low voltage switchgear via RUNN.
To protect the transformer substation KTP from overloads, short circuits, voltage surges, lightning and applied voltage limiters, different switches with fuses, circuit breakers.
In order to avoid the possibility of electric shock, staff, workers and others, our company in the production of KTP, all equipment places in the body, made of metal. Such a body is equipped with electrical and mechanical locks.
Metal transformer substation space divided into compartments. One Bay for high-voltage equipment, switching and protection. The other step-down transformer compartment and low voltage switchgear.
In order to monitor the quality control of electricity, KTP is equipped with test equipment (such as pointers, voltage devices for measuring voltage and current) and electricity meters.
When installing substation KTP you must observe the following rules:
|Distance from non-insulated voltage 6-10 kV current-carrying parts must not be less than 4.5 m and 0.4 kV voltage not less than 3.5 m.||You must delete the passage of vehicles between the KTP and feet of overhead lines.|
LLC "Plant substation recommends you the following related products: transformers with audit ТМG TMZ ТМН TRANSFORMER TM
TM 10 160 (6) 04
CMG 160/10 (6)/0.4