- BrandБерезовский Завод Подстанция
- Country of manufactureRussia
Transformer substation Ktpn 63
Appointment Of KTP
Complete transformer substations KTP are intended for converting electricity to reduce high voltage 6 or 10 kV to 380 (220) Volt. They are used to supply industrial and household consumers.
To use 63 Ktpn requires transformer TM 63/10 (6)/0.4Device KTP
Step-down power transformer-core element of transformer substation. It can be oily or dry. This transformer is connected through an input device, by the higher voltage IOC. Connects oil or dry type transformer for air or cable input high voltage line. Electricity consumers will connect to the reducing the transformer from the low voltage switchgear via RUNN.
To protect the transformer substation KTP from overloads, short circuits, voltage surges, lightning and applied voltage limiters, different switches with fuses, circuit breakers.
In order to avoid the possibility of electric shock, staff, workers and others, our company in the production of KTP, all equipment is placed in the casing, made of metal. Such a body is equipped with electrical and mechanical locks.
Metal transformer substation space divided into compartments. One Bay for high-voltage equipment, switching and protection, another down-Bay power transformer and switchgear low voltage.
In order to monitor the quality control of electricity, KTP to equip test equipment (such as pointers, voltage devices for measuring voltage and current) and electricity meters.
When installing substation KTP you must observe the following rules:
|Distance from non-insulated voltage 6-10 kV current-carrying parts must not be less than 4.5 m and 0.4 kV voltage not less than 3.5 m.||You must delete the passage of vehicles between the KTP and feet of overhead lines.|
LLC "Plant Substation" draws your attention to the related products: transformers with audit TM, CMG, TMZ, ТМН, TRANSFORMER
TM 63 10 04
CMG/10 63 (6)/0.4